Leaking from roof above a new apartment, in Bulimba, an Eastern suburb of Brisbane,
Roof leak above a new apartment. Identified by Peter Weddell, owner/operator of Qld Home Buyers Inspection Service and Queensland Building Inspection Service, QBIS.
Problem with leaking:
Copious amount of sealant have been applied between the roof flashing’s and sheeting indicates leaking has occurred from this roof, most likely on a number of occasions.
The flashing’s were removed and replaced with wider and properly fitted ones, this eliminated the problem.
A considerable amount of sealant has been applied to this relatively new roof above a unit in Bulimba near the Brisbane river.
This is only masking the problem for the short term, not fixing it.
Water has pooled to top side of the exhaust vent, this will allow for further leaking and premature rusting.
Roof leaking above new unit, recommended rectification:
A modified flashing would be required to allow the water to flow around the vent,
Sealant breaks down from UV, it may also crack from different rates of expansion and contraction between the flashing’s and roof sheeting.
Related material on roofs and maintenance
Government on Repairs and maintenance
For independent Building Inspections Brisbane in all suburbs, Qld Home Buyers Inspection Service. qbis.com.au